Control Cable with Cu Core, XLPE Insulation, PVC Sheath, Copper Tape Shielding
It is used as connection cable of electric appliances and instruments for power distribution devices of rated voltage 600/1000V.
State standard GB9330-88
1. Temperature for installation & min. Bending radius: Preheating is unnecessary when ambient temperature remains no lower than 0º C. Installation is free from restriction by drop. And min. Bending radius of cable is stipulated as follows:
A) It will be no less than 6 times that of cable OD for cable without armor.
B) It will be no less than 12 times that of cable OD for cable with armor or that with copper tape shielding.
C) It will be no less than 10 times that of cable OD for soft cable with shielding structure.
2. Long-term working temperature of conductor is 90º C.
3. Max temperature of cable conductor is no more than 250º C during short circuit within 5s.
Send Inquiry to this Member
Related Products of this Company
This member assumes full responsibility for the content of this listing. DIYTrade accepts no responsibility whatsoever in respect of such content.
To report fraudulent or illegal content, please click here
China Suppliers Quick Searching: